4-14 LIGHT/LAMP ASSEMBLY MAINTENANCE.
This task covers:
Tool Kit, General Mechanics
(item 1, Appendix B)
Soldering Gun GT7A-3
Both generator sets shut down.
Hand Operated Terminal Crimping Tool
Switch box cover open.
Insulation Sleeving, Heat Shrinkable
1. Measure for continuity between terminals (5, Figure 4-11). If continuity exists, replace lamp housing.
2. Measure for continuity of indicator light assembly leads (7) between terminals (5 and 8) in accordance with
Figure 4-11. Light/Lamp Assembly.