(b) The ON LINE light (7) or (3) for the other generator set should be off.
(9) If lights fail to go on or off, repeat steps (6), (7), and (8). If lights do not function properly, report
the problem to the next higher level of maintenance.
b. The second generator set is now supplying electric power to the connected load. All
SYNCHRONIZING lights (1) should be dark.
c. Refer to TM 9-6115-639-13 and set AC CIRCUIT INTERRUPTER switch for generator set that is now
off line to OPEN position.
d. Check that switch box ON/OFF switch (6 or 4) for the off line generator set is at center position.
e. Refer to TM 9-6115-639-13 and:
(1) Shut down generator set that is now off line.
(2) Using generator set VOLTAGE adjustable rheostat, adjust voltage of generator set that is now on
line to the desired value.
f. Refer to Table 2-2 and perform "After" PMCS for the generator set that was shut down.
g. For the generator set that is now ON LINE, perform the PMCS listed as "During" in Table 2-2.
2-5.3.3 Stopping Generator Set.
a. Set the switch box ON/OFF switch (6 or 4, Figure 2-8) for the generator set to be stopped to OFF
b. Stop the generator set in accordance with TM 9-6115-639-13.
c. Perform the generator set PMCS listed as "After" in Table 2-2.
IDENTIFICATION AND INFORMATION PLATES.
AN/MJQ-42 Identification/Transportation Data Plate. Refer to Figure 2-9. This plate is located on rear
of curbside fender.
Figure 2-9. AN/MJQ-42 Identification/Transportation Data Plate.