Generator Set Operating Procedures. Refer to TM 9-6115-639-13.
Trailer Operating Procedures. Refer to TM 9-2330-202-14&P.
Power Plant Switch Box Operating Procedures.
2-5.3.1 Operating a Single Generator Set.
a. Perform the Preventive Maintenance Checks and Services (PMCS) listed as "Before" in
b. Check that both ON/OFF switches (4 and 6, Figure 2-8) on switch box are at center position.
c. Check that TRANSFER switch (5) on switch box is at bottom position.
Figure 2-8. Power Plant Operation.
d. Refer to TM 9-6115-639-13 and:
(1) Start one of the generator sets.
(2) Use generator set VOLTAGE adjustable rheostat to adjust voltage to required value.
(3) Set AC CIRCUIT INTERRUPTER switch on the operating generator set to CLOSED position.
e. Check switch box to make sure that GEN SET ON light (8) or (2) is lit for generator set just started.
f. Set switch box ON/OFF switch (6) or (4) below lit GEN SET ON light to ON position.