Figure 11-10. Obtaining Dimension C
unusual noises such as produced by parts rubbing
When generator installation has been
completed and inspected, install covers and
Repair. Repair of the generator consists of
testing, removing, replacing, and repairing
components as listed in table 11-1.
Replace or rebuild all defective parts.
To remove coils from an iron core, it is
recommended that the part be heated in a
moderate oven temperature 302°F (150°C) to
facilitate removal. Single coils should not
be replaced as adjacent parts of the winding
may be damaged during, coil removal.
Apply varnish to any damaged areas of
Replace damaged exciter rotor or stator.
Overhaul. Overhaul of the generator consists of