1. Wiring harness
2. Wiring harness
6. Wiring harness
7. Control cubicle
Fault indicator panel
Cover(Class 1 sets)
Screw, stop lever
21. Manual control
Figure 3-17. Generator Set Controls
(2) Unscrew fuse holder cap (24) and remove
fuse (25). Install new fuse and replace fuse holder
3-104. Control Cubicle Assembly.
See figures 3-18, 19 and 20, and proceed as follows:
a. Inspection. Inspect the generator control
cubicle for defective, broken, cracked, or otherwise
b. Testing. Testing of components of the control
cubicle is described under the appropriate heading
in paragraphs 3-105 through 3-130.
c. Repair. Repair by replacement of components
which do not function properly during testing.
C h a n g e 1
24. Fuse holder cap
26. Test or reset
27. Dc control
Turn engine off and remove the
battery negative connection be-
fore removing any electrical
leads to avoid possible short
circuit and resulting damage.
d. Replacement. If a component needs replace-
ment, gain access to the rear of the control cubicle
panel (96, fig. 3-18) by loosening the three quarter-
turn fastener and permitting the control cubicle panel
to pivot about its hinges in a forward direction. Re-
place control cubicle panel components which do not
function properly in step b (testing) as indicated in
following paragraphs. Replace control box (123, fig.
3-18) as described in paragraph 3-135 b.
3 - 3 8