Insert terminal lug end of power cable (3 or 4) into stuffing tube assembly (13) and slide forward until
end of power cable outer covering is visible inside switchbox (1).
Slide seal (12), washer (11), and stutling tube compression nut (10) forward and tighten compression
Remove hex nut (6) and internal tooth washer (7) from load terminal
Install internal tooth washer (7) and hex nut (6). Tighten hex nut.
Repeat steps 4 and 5 for ground terminal and ground lead.
L0 (9) and install lead
Remove nuts (5, figure 4-10), lock washers (6), and flat washers (7) from contactor terminal (9) of
contactor associated with power cable being installed.
Connect power cable lead marked L1 to contactor terminal A2, lead marked L2 to contactor terminal
B2, and lead marked L3 to contactor terminal C2.
Install flat washers (7), lock washers (6), and nuts (5) on contactor terminals (9). Tighten nuts.
Install contactor terminal shield (4), lock washers (3), and screws (2).
Close switch box cover (1) and secure with clamping catches (11).
Repeat steps 1,2, and 3 above and install other end of power cable in stuffing tube on generator set.
Connect leads to generator set load terminals as follows:
Lead Marked to Generator Set Load Terminal
Place clamps (5, figure 411) on replacement power cable (3 or 4) and existing ground wire going from
switch box-ground-terminal and trailer ground stud, and install flat washers (4), screws (3), and self-
locking nuts (6).