Figure 4-10. Power Cable Connections to Switch Box Contactors.
4. Use multimeter to check for shorts in power cable. Check for continuity between ground and L0, L1,
L2, and L3; L0 and L1, L2, and L3; L1 and L2, and L3; and L2 and L3. Continuity in any of these
tests indicates a shorted cable which must be replaced.
5. Close switch box cover (1) and secure with clamping catches (11).
1. Disconnect electrical leads and ground lead from generator set.
2. Pull power cable from stuffing tube.
a. Remove stufiing tube compression nut (8, figure 4-11) from stuffing tube body (11).