ARMY TM 5-6115-633-14&P
Insert four screws (3), four Iockwashers (4), four flat washers (5) and four beveled
washers (6) down through generator set skid into nuts welded to underside of mounting
Position beveled washers (6) so that screw heads are parallel to tops of washers. While
holding beveled washers in position, tighten hardware to secure generator set (2) to
Insert engine oil drain hose (9) through grommet in trailer bed (8).
Section IV. MAINTENANCE OF ELECTRICAL SYSTEM
5-6. Switch Box Repair. (See figure 5-8.) Repairs to the switch box require disconnecting wires.
When reconnecting wires, refer to the schematic inside the switch box (figure 4-7 or 4-8, as
any repairs on switch box. Failure to observe this precaution may result in
injury or death by electrocution.
a. Switch Replacement.
Replacement switch will have unmarked terminals and will have to be
compared with original switch.
Remove 16 screws (1), 16 Iockwashers (2) and 16 flat washers (3) securing cover (4)
to switch box (5) and take cover, with switch (6) attached, off switch box.
Make sure identification bands on wires are legible before disconnecting wires
from switch. Tag switch terminals and all unmarked wires.
Disconnect all wires from switch (6) by removing one screw (7), one nut (8) and one
star washer (9) from each switch terminal.
Remove screw (10) and Iockwasher(11) securing knob (12) to switch (6) and take off
Remove four screws (13), four nuts (14), eight flat washers (15) and preformed
packing (16) securing switch (6) to cover(4) and take switch off cover.