P-9-TM-457-35 T.O. 35C2-3-442-2
TM-07464A-35 TM 5-6115-457-34
Figure 6-45. Overload Relay (K14), test setup
6-178. TACTICAL RELAY BOX (A29).
Exercise extreme care not to
6-179. ON EQUIPMENT TEST.
touch exposed electrical connec-
tion when working inside tactical
a. Symptom and Isolation of Malfunc-
tion. A malfunction of the tactical relay
box is usually indicated by a failure of the
overvoltage relay, reverse power relay,
short circuit relay, and overload relay.
Remove cover from tactical relay
To isolate the malfunction, refer to figure
box to gain access to test points,
1-18 and proceed as follows.