Figure 4-7. Power Cable Connections to Switch Box Contactors.
4. Use multimeter to check for shorts in power cable. Check for continuity between ground and N, L1,
L2. Continuity in any of these tests indicates a shorted cable which must be replaced.
5. Close switch box cover (1) and secure with clamping catches (11).
1. To disconnect electrical leads and ground lead from generator set refer to Figure 4-1 or Figure 4-8 and
reverse the procedures of connecting the power cables as listed in paragraph 4-2.2.1.