5-55. LOAD TERMINAL ASSEMBLY . See Figure 5-41.
Place load terminal (4) in position in the outgoing power enclosure (14) and secure with four capscrews (12) and
Reconnect the ground wire (8) on the load terminal (4) and secure with screw (11) and two nuts (10).
Reinstall the load terminal insert (9).
Reconnect the ground wire (8) to the load terminal insert (9) and secure with screw (7), washer (6), and nut (5).
Reconnect the load cable (3) to the rear of the load terminal (4) and secure with nut (1) and washer (2).
Remove danger tag from MAINTENANCE LOCKOUT switch S100 and set switch to OPERATE.