TM 5-6115 400-12
STEP 4. AFTER ENGINE HAS STOPPED, PULL DC
POWER CIRCUIT BREAKER TO OPEN.
STEP 1. REMOVE LOAD (PUSH CIRCUIT BREAKER
STEP 2. ALLOW ENGINE TO OPERATE FIVE (5)
SWITCH TO OPEN POSITION).
MINUTES AT NO LOAD
STOP ENGINE BY PUSHING ENGINE
SWITCH TO OFF POSITION
Figure 2-8. Stopping instructions.
(4) voltage change boards of both units for the
synchronizing lights are on. Damage
to one or both sets may result.
(5) Designate one unit as the operating unit and
d. Removal from Parallel Operation. Refer to
connect the load cable to this unit. Consider the
other unit as incoming unit.
sets in parallel.
parallel operation, see that the load
When parallel switch of each unit is
does not exceed the full rating of the
on the synchronizing lights of
Synchronizing lights of operating
unit should remain off.
stop remaining set or sets before
Do not close the circuit breaker of
detaching load terminal wires or