2-3.4.2 Power Unit. Connect load cables to generator set load terminals. Refer to operating instructions in TM 9-6115-
2-3.5 Positioning of Fire Extinguishers. Remove fire extinguisher(s) from bracket(s) on trailer. Locate fire
extinguisher(s) on ground away from power plant/power unit.
2-4 INITIAL ADJUSTMENTS, CHECKS, AND SELF TEST.
Refer to table 2-2 and perform all "Before" PMCS. Refer to TM 9-6115-642-10 and perform generator set initial
adjustments, checks, and self tests.
2-5 OPERATING PROCEDURES.
2-5.1 Generator Set Operating Procedures. Refer to TM 9-6115-642-10.
2-5.2 Trailer Operating Procedures. Refer to TM 9-2330-202-14&P for Power Units PU-798 and PU-799, TM 9-2330-
392-14&P for PU-798A and PU-799A, and TM 9-2330-213-147P for Power Plants AN/MJQ-37 and AN/MJQ-38.
2-5.3 Power Plant Switch Box Operating Procedures.
2-5.3.1 Operating a Single Generator Set.
Perform the Preventive Maintenance Checks and Services (PMCS) listed as "Before" in table 2-2.
Check that both ON/OFF switches (4 and 6, figure 2-9) on switch box are at center position.
Check that TRANSFER switch (5) on switch box is at bottom position.
Figure 2-9. Power Plant Operation.
Change 2 2-35