SHORT OPERATING INSTRUCTIONS
EG 150KW / EPP 2 x 150KW / 400Hz,120/208V
Check all cable connections between EPP and power distribution unit (PDU).
Connect EPP to ground.
Connect potential equalization cables to PDU and to the load.
Connect exhaust hoses.
Perform a visual check of the engine and generator.
Check oil level and top up to maximum if required.
Turn MASTER SWITCH to ON.
Perform lamp test.
Check fuel level and top up if necessary.
10. Check gauges and meters.
Uncoil and connect power supply and control cables.
Starting the generator
Ambient temperature >0 ° C
Turn GLOWPLUGSTART switch to the far right position, and hold (max. 30
engine is running.
Ambient temperature between 0 ° C and -30 ° C
Turn GLOWPLUGSTART switch to center position and hold until GLOWPLUG ON l
amp lights up
(approx. 90 sec.); then turn GLOWPLUGSTART switch to extreme
right position until engine is running.
After starting the unit
All fault indicators must be OFF.
Hourmeter is ON.
Oil pressure indication must be within the range of 3 - 5 bar.
30 sec. after the unit is running
Check the frequency indication (400 Hz).
Check output voltage by using the voltage selector switch.
L1 -N; L2-N; L3-N = 120 V
L1 42; L2-L3; L3-L1 = 208 V
Figure 2-17 Generator Set 150 kW Short Operating Instructions Plate (sheet 1 of 2).
2 - 51