ARMY TM 9-6115-604-12
NAVY NAVFAC P-8-633-12
Table 3-2. Operator Preventive Maintenance Checks and Services. (Continued)
Not Fully Mission
After generator set is started and operating normally, set
TIMER on battery charger panel (generator compartment
above batteries) to a full 24 hours.
Monitor control room instruments not less that once per
hour. (Record readings, if required.) Refer to Table 2-1,
Table 2-2, and Table 2-3 for normal instrument readings
under rated load. (If using RCM, refer to Table 2-13 ) Be
alert for trends or changes in readings that could Indicate
developing problems. Be especially alert for unequal volt-
age or current between lines, uneven generator tempera-
ture readings, uneven exhaust temperature readings; ris-
ing, falling, or fluctuating frequency output.
Empty accumulated debris from cup assemblies at bottom
of each air cleaner.