T O 35C2-3-442-2
Figure 6-6. AC current meter (M8) test setup
e. Check resistor for continuity and
proper ohmic values.
a. Clean electrical components and in-
struments with a clean lint-free cloth
moistened in an approved cleaning solvent
and dry thoroughly.
g. Inspect terminal lugs for security
Cleaning Solvents are flammable and
moderately toxic to skin, eyes and
h. Inspect wiring for defective insula-
respiratory tract. Eye and skin
tion and electrical connectors for damaged
protection required. Good general
threads; bent, loose, or missing pins.
ventilation is normally adequate.
Check each harness wire from connector
b. Clean metal parts in unapproved
cleaning solvent and dry thoroughly.
to case and surrounding pins.
i. Inspect sheet metal parts for bent
c o r n e r s , distortion, cracks, tears, and
Figure l-6 is the schematic for the
6 - 3 4 . REPAIR.
a. Straighten dents or distorted areas
of the box using proper tools.
a. Inspect meters and gauges for dam-
aged cases and faces.
Welding operations produce heat,
b. Check switches for continuity.
highly toxic fumes, injurious
c. Inspect terminal boards for cracked
borne particles. Welding gog-
gles, with proper tinted lenses,
insulation, stripped threads, and missing
apron or jacket and welder's
boots are required.
d. Check capacitors for opens and
b. Minor cracks may be repaired by