Table 2-2. Operator Preventive Maintenance Checks and Services (continued)
Observe the following indicators and ensure
they are operating properly.
OIL PRESSURE 25-60 psi (172-414-kPa)
VOLTAGE 120-240 VAC
Inspect ground rod and cable for loose
connections, breaks, damage and
Cable is missing or
a. Check door, panel, hinges, and clamping
catches for damaged, loose, or corroded
b. Inspect air intake and exhaust grills for
Check to ensure identification plates are
Inspect skid base for cracks and corrosion.
Skid base is
cracked or shows
signs of structural
The fuels used in this generator set are flammable. Do not smoke or use open
flame when performing maintenance. Flames and explosion can occur resulting in
severe personal injury or death.
Check for loose, damaged, or missing
Inspect fuel system for leaks, and
Damaged, loose, or missing hardware.
Any fuel leaks, and
damaged, loose, or
a. Inspect fuel filter/water separator for
leaks, cracks, damage, improper mounting,
or missing parts.
b. Drain water from fuel filter/water separator.
Any fuel leaks.