ARMY TM 9-6115-464-12
AIR FORCE TO 35C2-3-445-1
NAVY NAVFAC P-8-624-12
Figure 2-4. Load Terminal Board Assembly
GENERATOR SET CONVERSION INSTRUCTIONS.
To convert the generator set for operation at 120/208 Vac or 240/416 Vac, proceed as follows.
Do not attempt to alter position of the voltage reconnection board while the
generator set is operating. Make sure that the generator set is not paralleled
to another which is operating. Failure to observe this warning may result in
death by electrocution.
(1) Remove 12 mounting nuts (Figure 2-7) and locate the movable board until the arrow at its edge mates
with the arrow on the stationary board indicating the desired operator voltage.
(2) Install and tighten the mounting nuts.
b. To convert 50/60 Hz precise set to 50 Hz operation, place frequency select switch (Figure 1-4) on precise
relay assembly to 50 Hz position.