2.3.5 Installation Instructions.
18.104.22.168 Connect Battery Cable.
Below 32 °F (0 °C) the battery sets of two Generator Sets 150kW can be connected in parallel to increase capacity;
below -22 °F (-30 °C) the battery sets must be connected in parallel. The battery cable is used to connect the two sets
a. Connect battery cable as follows:
Remove protective cap (1, figure 2-11) from J3 SLAVE RECEPTACLE 24 VOLTS.
(2) Connect battery cable (2) to the J3 SLAVE RECEPTACLE 24 VOLTS of each Generator Set 150 kW.
Figure 2-11 Connect Battery Cable.