Section III. OPERATION UNDER USUAL CONDITIONS
INITIAL ADJUSTMENTS, CHECKS, AND SELF TEST.
2.3.1 Initial AdjustmentS.
The Generator Set 150 kW requires no initial adjustments.
2.3.2 Checks and self test.
184.108.40.206 Control Cabinet Assembly Lamp Test.
Before operating the unit: perform steps a through d.
During operation of the unit: perform step d.
Open flap (1, figure 2-6) and set MASTER SWITCH (10) to ON.
a. Turn PANEL DIMMER switch/potentiometer (8) all the way to the right.
b. The following lamps must light up:
The three front panel lights (2)
BATTERY CHARGING CONTROL (3) and OIL PRESSURE (4)
c. The following meters must be illuminated:
OIL TEMPERATURE (5), OIL PRESSURE (6), and FUEL LEVEL (7)
d. Pressure LAMP TEST pushbutton (9):
All lamps on front panel must light up.
e. If any lamp fails to light, refer to the next higher level of maintenance.
220.127.116.11 Cabinet Light
1. Proceed as follows to test the light installed in the cabinet:
Remove the key from the left side of the front panel and using the key turn the four front panel quick-release
fasteners to the right to unlock them.
b. Open the front panel to the right, set the front panel prop to keep the panel open and check that the light installed
in the cabinet lights up.
c. If lamp fails to light, refer to the next higher level of maintenance.
d. Close the front panel and turn the four front panel quick-release fasteners to the left to secure them. Return key
e. Close flap (1, figure 2-6).
(2-33 blank)/2-34 Change 1