2. Start generator set.
a. Adjust voltage and frequency to rated values.
Close the AC circuit interrupter on the generator set.
3. At EPP-III-EPU junction box, set ICC, CRG or ECS ON/OFF switch to ON.
Observe that the INPUT POWER indicator on the side of junction box Is illuminated.
Observe that the appropriate shelter indicator is illuminated.
Observe that the appropriate GENERATOR ONLINE indicator is illuminated.
If indicators in a. through c. above do not illuminate, check to insure all switches are in the on position, all
cables are tight, and no lamps are burned out.
4. At load bank:
a. Set BLOWER/CONTROL POWER switch on the load bank to ON.
Set POWER switch on digital display panel at the load bank to ON.
c. Select desired load using KW LOAD STEP switches.
Do not apply Instantaneous (one step) loads greater than 50 kW on the EPP
Ill 150 kW generator set.
Do not exceed the 30 kW rating on the PU-789/PU-804 30 kW generator set.
d. Apply load by turning MASTER LOAD to ON.
e. Observe function display for appropriate indication.
Operate each of the 150 kW generator sets for approximately 30 minutes after reaching 100 percent load.
If the appropriate indications are not displayed, check to insure that all switches are in the correct position
and all cables are tight. Refer to the appropriate maintenance procedures.
5. At generator set:
Observe voltage, frequency, and load meters for proper indications.
If proper indications are not present on any meter, refer to the appropriate maintenance procedures.