5.21 POWER SUPPLY NT2 24 V~ MAINTENANCE.
This task covers:
General Mechanics Tool Kit
(item 2, appendix B)
Generator Set 150 kW shut
Automotive Fuel and Electrical System Repair, Tool Kit
(item 3, appendix B)
Disconnect the negative battery cable first and then the positive bat-
tery terminal cables. Failure to observe this warning could result inse-
vere personal injury or death.
Tag all cables prior to removal to ensure correct connection of the cables
Open flap (2, figure 5-37) on unit hood assembly (1).
Open front panel (4) and secure with prop (5).
Removal procedure for all power supply components NT2 24 V~ is
the same as for time relay K106, described below.
Remove time relay K106 (27) as instructed in paragraph 5.20.
On power supply component (28), push locking elements toward each other in direction of arrow
and pull power supply component NT2 24 V~ (34) out of time relay K106 (27).
Installation procedure for all power supply components NT2 24 V~
is the same as for time relay K26, described below.
Insert power supply component NT2 24 V~ (12) into time relay K106 (27).
Install time relay K106 (27) as instructed in paragraph 5.20.
Stow prop (5) and close front panel (4).
Close flap (2).