Section III. MAINTENANCE PROCEDURES
This section will provide authorized direct support level maintenance instructions for the Generator Set
150 kW and its components. Each major component will be covered under its own paragraph heading.
Each paragraph will be further divided into specific maintenance tasks, as directed by the Maintenance
Allocation Chart (MAC). These tasks will include inspection, testing, service, adjustment, removal, disas-
sembly, assembly, repair, replacement, and installation, as applicable. Step by step instructions and spot
illustrations will guide personnel through each maintenance task.
Potential 150 kw shock hazard with failure to adhere to this warn-
ing. Contact with this high power could result In death or severe
injury. if the removal of one generator from the EPP iii Is required,
replace it with an extra generator. Always make sure that two gen-
erators are mounted to the EPP Ill. Continued use of the EPP III with
only one generator could result in a catastrophic shock hazard.
Do not operate one of the EPP-III generators when the other gener-
ator Is dismounted.
Prior to energizing the equipment the operator must check for ex-
posed electrical terminals.
Always install protective covers on control and power cables
when cables are not connected.
Be sure to observe ail warning signs on equipment.
Disconnect the negative battery terminal cable if task Involves
Remove the ignition key while working around the engine.
For safety reasons, work on the GEN SET 150 kW must always be
performed by two persons.
A notice will indicate when three persons are required for a particu-