2.5.2 Generator Set 150 kW Shutdown.
Open Flap (1, figure 2-19).
126.96.36.199 Normal Shutdown.
Press AC CIRCUIT INTERRUPTER OFF pushbutton switch (3):
Lamp in AC CIRCUIT INTERRUPTER ON illuminated pushbutton switch (2) goes out.
Before shutting down Generator Set 150 kW, allow It to operate for five
minutes with no load applied.
Turn MASTER SWITCH to OFF (4). Pull key ¼ to ½ way out from MASTER SWITCH.
Perform the Preventive Maintenance Checks and Services (PMCS) listed as AFTER in table 2-4.
Figure 2-19 Generator Set 150 kW Shutdown.