ARMY TM 9-6115-604-12
NAVY NAVFAC P-8-633-12
Figure 3-7. Main Disconnect Switch S120
Maintenance of Station Power Cable Assembly
(1) Inspect. See Figure 3-9 Perform visual inspection on station power cable assembly as follows:
(a) Inspect plug connector for deformities, cracks, and other damage. Check that the female terminals
inside the connector are clean, free from any obstruction, and not damaged.
(b) Check securing nut on plug connector against mounting hardware on J1 01 on the generator set for
possible cross-threading or damage.
(c) Check that the cable grip is securely fastened to the cable insulation sleeve. Check that the tie-down
loop on the cable grip Is functional.
(d) Lay out cable and inspect station power cable insulation throughout Its entire length Check for cuts,
cracks, ruptures, or deformities indicative of internal cable breakage.
(e) Check that the station power cable marker band is clearly legible and securely attached to the power
(2) Replace. Replace defective station power cable. Refer to the next higher level of maintenance for repair.
Disconnect all power and remove outgoing power cables before performing
inspectlon. Put cables in park position.