ARMY TM 9-6115-464-34
AIR FORCE TO 35C2-445-2
NAVY NAVFAC P-8-624-34
GENERATOR SET TESTS AFTER OVERHAUL REPAIR INSTRUCTIONS
Section I. INSPECTION
a. The activity performing the repair or overhaul is responsible for the performance of all applicable tests and
inspections specified herein. Activities performing maintenance on any portion of the generator set must
perform those tests and inspections required by the applicable component or system repair instruction.
b. A thorough inspection of the generator set shall be conducted to insure that workmanship and materials
c. The inspection shall be conducted each time the generator set is overhauled or rebuilt.
4-2. HOUSING AND FRAME INSPECTION.
a. Check that lifting eyes are installed and firmly secured.
b. Check that drain holes are open to prevent moisture accumulation.
c. Insure that exposed parts are properly treated to resist corrosion.
d. Open and close panel doors, engine area doors, and generator area doors to insure proper installation
and freedom of motion.
e. Inspect movable door gasketing to insure that it is weatherproof.
f. Check that all caps and covers are equipped with ties, chains, or other ties to prevent loss.
4-3. ENGINE INSPECTION.
a. Check mounting bolts of all components and accessories to insure that they are firmly secured.
b. Check designation and data plates for legibility.
c. Insure that fuel and hydraulic oil lines are protected from damage due to vibration.
4-4. GENERATOR INSPECTION.
a. Insure that generator leads are properly identified and protected from damage due to vibration.
b. Insure that inspection openings are protected by screening or protective plates.
c. Check that the engine generator screws are firmly secured. See paragraph 1-10v, for proper torque
4-5. ELECTRICAL ACCESSORIES INSPECTION.
a. Check all cable and harness assemblies for secure fastenings and protection against chafing and
b. Insure that all cable and harness connectors are firmly secured in their proper place.