ARMY TM 9-6115 464 34
AIR FORCE TO 35C2-3-445-2
NAVY NAVFAC P-8-624-34
Pull all slack from the leads and tighten the clamping screws of lead block.
Secure lead block and gasket to end bell assembly using lockwashers (8) and
Using a suitable lifting device stand the stator assembly on the end bell
Use blocking as necessary to maintain stator in the vertical position.
Remove the lifting eye bolt from the stator and install it in the coupling disc end.
Use extreme care when installing rotor to avoid damage to the generator wind Failure to observe this
caution could result in equipment damage.
Using a suitable lifting device, install the rotor (25) into the stator (26).
Temporarily secure rotor to stator as in disassembly (see figure 3-137).
Carefully set the stator on its mounting feet.
Press new bearing (23) onto adapter (24).
Install bearing and adapter and secure with a flat washer and screw (18).
Remove screw and replace flat washer with lockwasher (19). Torque screw;
Install bearing housing (22) and secure with lockwashers (21) and screws (2) 31 ft-lbs.
Center bearing housing in end bell prior to torquing screws.
Install screen guard (13) and secure with lockwashers (12) and screws (11).
Install cover (16) and secure with lockwashers (15) and screws (14).
Install cover (17) into bearing housing.
Install screen guard (6) and secure with lockwashers (5) and screws (4).
Install drip cover (3) and secure with lockwashers (2) and screws (1).
Remove steel bar securing rotor to stator and install lifting eye bolt on generator.
Testing. Perform winding resistance test, high potential test, and insulation resistant equipment and procedures
specified in Military Standard MIL-STD-705.
Installation. Refer to paragraph 2-7c for generator installation procedures.
3-96.1. The field flash circuit consists of the following components:
K5 Relay (located on A5 board)
Current Limiting Resistor
3-310 Change 1