PU 794/G, TROUBLESHOOTING PROCEDURES
TEST OR INSPECTION
PU 794/G WILL NOT START USING REMOTE CONTROL UNIT, BUT STARTS WITH
SHORTING PLUG INSTALLED.
PU 794/G must be shut down before checking cable
Failure to do so could result in
serious injury or death by electrocution.
Connect 5-foot control cable from connector plate to unit 2
control connection on junction box. Attempt to start unit
with SET No. 2 controls on remote control unit.
PU 794/G must be shut down before disconnecting
remote control unit.
Serious injury or death by
electrocution could result if procedure is
performed with power unit running.
If the unit starts, the remote control unit is faulty.
Replace the remote control unit.
PU 794/G must be shut down before performing all
injury or death
Test the control
to do so could result in serious
cables, remote control cable and junction
Replace faulty cable or junction box.
If unit still will not start, the remote functions box
assembly is faulty.
Report to intermediate direct support maintenance.