Table 9-1. Test Schedule
c. Test Procedure.
Test Method (MIL-STD-705)
Record only the readings of the master
and panel instruments at no-load, 50%
and 100% of rated load. Record the
readings of the master and panel in-
struments at all voltage connections.
(1) Position switches as follows:
(a) Master switch-stop.
(b) Panel light switch-off.
Accuracy shall be as follows:
Current indicator system, 10% max.
Voltage indicator system - Initial
accuracy 2. 5% of full scale except that
within the ranges of 115 to 125 and 200
to 250V. The error shall not exceed 3
and 5 volts respectively.
Frequency indicator system 0.5%
Voltage adjust range shall be between
197.6 and 218. 4V for the 120/208V, 3
phase 4 wire connection between 114
and 125V for the 120V, 1 phase, 2 wire
connection between 228 and 252V for
the 120/240V, 1 phase, 3 wire connec-
Figure 9-1. Adjusting R3 Resistor
Figure 9-2. Testing Engine Control Circuitry