Figure 3-17. Engine Cooling Assembly (Sheet 2 of 2)
3-23. GENERATOR ASSEMBLY.
On ASK equipped generators, inspection is limited to screen
guard areas visible through access doors. Inspect screen
guard (3, figure 3-18) to see that it is clean and free of
Figure 3-18. Generator Assembly
debris and free of dents or cracks. Check that screen-guard
is securely fastened in place over opening in generator
housing-stator assembly. Inspect end-bell (2) to see that it is
clean and free of cracks or other physical damage. Check
that openings in end-bell and end-bell cover are free of
debris. Check that end-bell is securely attached to generator
3-24. ENGINE ASSEMBLY.
a. Lifting Attachment (sea figure 3-17). On ASK equipped
generators, open air intake door. Inspect for cracks or other
physical damage. Check that mounting screws (37) are secure.
On ASK aquipped generators, if intake manifold is
suspected of possible problems, refer to higher level
b. Intake Manifold Assembly (see figure 3-19). Inspect intake
manifold (1) for cracks or physical damage. Check that manifold
is properly secured to cylinder head and mounting screws (5)
and lock tabs (3) are in place.
c. Oil Drain Hose (see figure 3-20). On ASK equipped
generators, remove oil access door. Inspect oil drain hose for
physical damage. Check that drain valve operates properly and
does not leak when closed. Check that oil drain hose is properly
stored when not in use.
d. Engine Mounting Assemblies (Two) (see figure 3-19). On
ASK equipped generators, remove oil access door and batteries
access door. Inspect engine mounts (13) for deterioration or
physical damage. Check for accumulation of dirt, fuel, or oil.
Check that mounts are securely attached to engine and to skid-
bsse with all mounting hardware in place.