(1) Panel Light. Panel lamp cover can be removed
for cleaning by turning them counterclockwise when
viewed from front.
(2) Panel Lamps. Panel lamps are screw in base
types and are replaceable.
3-20. FUEL SYSTEM (LESS TANK).
a. Inspect (see figure 1-1).
Inspect two fuel filter assemblies (10) for dents or other
physical damage. Check for leaks especially around fuel line
fittings (12), drains (1), and where bowl joins the head. Check
that fuel filter assemblies are securely attached to mounting
bracket (16) and that bracket is securely attached to bracket
support on skid-base.
( 2 ) F u e l S t r a i n e r A s s e m b l y ( s e e f i g u r e 3 - 1 3 ) .
Inspect strainer assembly (11) for dents or other phys-
ical damage. Check for leaks especially around fuel
line fittings (12), drain (1), or where the bowl joins the
(1) Fuel Filter Assemblies (see figure 3-13). On ASK
head. Check that strainer assembly (11) is securely
equipped generators, remove FUEL FILTERS access door.
attached to mounting bracket (16).
Figure 3-13. Fuel Filters and Fuel Strainer Assembly