(c) Check insulation for burns, chafing,
(b) Replace any heater element which does
not test correctly.
(4) Installation. Install heater element in re-
verse order of removal procedures.
i . Load Reject Relay. Visually inspect load
loose electrical connections, dents, cracks, and
evidence of shorting or other damage.
Do not use acid core solder on electrical
j. Wiring Harness.
(1) Removal. Tag and disconnect wiring
(4) Repair. Replace damaged wires, term-
harness wires, connectors, and terminals as re-
inals, and connectors by unsoldering connections,
quired for access to other components or replace-
installing replacement parts and soldering connect-
ment of damaged parts.
(2) Cleaning and Inspection.
(a) Clean wiring harness with filtered
If more than 30 percent of the wires
compressed air and a soft bristle brush or wipe
are damaged, replace the wiring
with a clean, lint-free cloth lightly moistened with
harness and forward it to higher level
an approved solvent.
(b) Visually inspect wiring harness for
(5) Installation. Install wiring harness in
burns, bent, corroded or otherwise damaged con-
reverse order of removal procedures.
nectors and terminals.