MATERIAL USED IN CONJUNCTION WITH THE GENERATOR SET
Section I. GENERAL
b. Check to see that all components are present.
This chapter contains instructions for operator and or-
c. Remove corrosion preventive compounds with an ap-
ganizational maintenance of material used in conjunction
proved cleaning solvent.
4-2. SERVICE UPON RECEIPT
d. Visually inspect all components for missing parts and
damage which may have occurred during shipment.
The following services shall be performed upon receipt of
material used in conjunction with the generator set.
e. Check all wiring for damage and loose connections.
a. Remove the equipment from shipping container.
Section II. FUEL BURNING WINTERIZATION KIT
The fuel burning winterization kit is used to preheat the
engine coolant and lubricating oil when ambient tempera-
ture is between -25F (-31.7C) and -65F (-53.9C). It
consists of a heater coolant pump, coolant circulating lines,
fuel line, electrical controls, wiring harness, and mounting
hardware. The heater burns fuel from the generator set
ter, right-rear of engine cylinder block. (Use impact wrench
coolant is pumped through the heat exchanger in the en-
gine oil pan, through the cylinder block, and returned to
(4) Remove plug (45) from right side of engine water
(5) Remove `WATER" plug (44) from center, left-rear
4-4. FUEL BURNING WINTERIZATION
of engine cylinder block.
STALLATION AND REPLACEMENT.
(6) Remove plugs (46 and 47) from engine oil pan heat
(7) Remove plate (48) located in skid base directly be-
low heater mounting space.
(8) Remove protective cap (49) from special relay as-
Disconnect battery negative cable before
installing fuel burning winterization kit.
(9) Remove cover (50) from heater control assembly
mounting hole located to the right of the control cubicle as-
If generator set is equipped with an elec-
installation of components which
Retain cover and attaching hardware. It
must be provided to accommodate both
is used to install heater control assembly.