(2) Visually inspect connector for corrosion,
(1) Clean load measuring unit with filtered
compressed air anda soft bristle brush or wipe
cracks, and bent or broken pine.
witha clean, lint-free cloth lightly moistened with
an approved solvent.
(3) Check electrical leads for burned, bent,
corroded, or missing terminals.
Visually inspect load measuring unit for
dents, corrosion, stripped or damaged
bent or broken connector pins, and evid-
(4) Check insulation for burns, shafing, and
shorting or other damage.
(3) Replace load measuring unit if damaged or
with a multimeter using figures FO-1 and FO-2.
c. Installation. Install load measuring unit in
reverse order of removal procedures.
3-117. GOVERNOR CONTROL
UNIT (Precise Sets
Do not use acid core solder on electrical
Inspect governor control unit for cracks, dents,
insecure connectors, insecure mounting, and evid-
d . Repair. Replace wires, terminals, and
ence of shorting or other damage.
connectors by unsoldering connections, installing
3-118. INTERCONNECTING WIRING HARNSSES.
a. Removal. Remove wiring harness termin-
als, wires, and connectors as required for access
to other components and to replace damaged parts.
If more than 30 percent of the wires are
damaged, replace the wiring harness and
Cleaning and Inspection.
forward it to higher level maintenance for
(1) Clean wiring harness with filtered com-
pressed air and an electrician's brush or wipe with
a clean, lint-free cloth lightly moistened with an
e. Installation. Install wiring harness in re-
verse order of removal procedures.