T O 35C2-3-446-1
c. Servicing an Engine on Standby.
(2) Replace the fuel filter elements at a maximum of 12
(1) Change engine oil and oil filter element at a
maximum of 6 months.
Section V. OPERATION UNDER UNUSUAL CONDITIONS
b. Cleaning. Keep the generator set and surrounding
IN EXTREME COLD (Below-
area as free of ice and snow as practical. Pay particular at-
tention to the fuel tank cap and filler neck.
a. General. The generator set is designed to operate
c. Fuel System. Keep the fuel tank as full as possible
in ambient temperatures as low as -25F (-31C) without
special winterization equipment. For operation at lower
temperatures, the engine must be heated by either a fuel bur-
with the proper grade of fuel for the existing ambient
temperatures. Service fuel stainer and filter assembly and
and 2-23 for operation instructions for these winterization
secondary fuel filter at more frequent intervals. At the end of
C h a n g e 11
U.S. GOVERNMENT PRINTING OFFICE: 1987- 754-030/60463